Bi-metal Lead Free Complete Water Temperature Control Station
LF Megatron - Megatron TM-26-LF
LEONARD MEGATRON® MODEL TM26LF Complete Water Temperature Control Station (1.0 - 26 GPM, 3.7 to 98 l/min) to include:
¾” bottom inlet connections (copper tube)
¾” top outlet connection (copper tube)
¾” return line size with piping method #2 (8 GPM maximum flow) see page 5 for piping options.
Thermostatic water mixing valve with DURA-trol solid bimetal thermostat (with Extended 7 Year Limited Warranty) directly linked to hot and cold valve porting, adjustable high temperature limit stop set for 120°F (49°C)*, color-coded dial: C-H, locking temperature regulator, integral checkstops. Full port ball valve, pressure gauge on mixed water outlet piping of large mixing valve. Dial thermometer (range:0 to 140°F, -10 to 60°C) and pressure gauge on mixed water outlet of the system. Outlet Test Connection with ball valve and ¾” hose connection with cap. Full port ball valve mounted downstream of test connection on mixed water outlet of the system. Inlet piping manifold with full port ball valves and dial thermometers (20 to 240°F, -7 to 116°C on hot supply, 0 to 140°F, -10 to 60°C on cold supply) on hot and cold supply inlets. Return piping, ¾”, with aquastat, circulator, dial thermometer (0 to 140°F, -10 to 60°C), balancing valve (with positive shutoff) to balance system, and check valve
Aquastat with temperature differential of 5 to 30°F (3 to 17°C) GFCI* switch. The GFCI switch will be used to turn the circulator on or off for setup. *Ground Fault Interrupter
Bypass piping, ¾”, with check valve and isolation ball valve to bottom port of small mixing valve. System mounted on strut, galvanized. Strut shall be assembled with three hole flat angle plate on corners, four hole tee plates or two hole flat plate connectors on all other support pieces using 3/8” grip lock nuts and 3/8”x 1” hex head cap screws, washers and lock washers. Factory pre-assembled and tested as a complete system.
All electrical connections to be completed by Electrical Contractor.
Valve assembly is certified to meet Low-Lead requirements of wetted surface area containing less than 0.25% lead by weight. All other fittings and components, the sum total of which comprise the wetted surface of this product, contain less than one quarter of one percent of lead by weight.